Many older, decommissioned coal power plants are being replaced with highly efficient natural gas turbines. In some places where fuel is imported, such as in Europe and Asia, highly efficient turbines are critical for power plants to continue operations because of high fuel costs. In the U.S., where natural gas prices are lower, highly efficient natural gas turbines are not only being selected as replacements for their cost savings, but also for their ability to meet stricter ambient emission regulations.
Twenty years ago, land-based electrical power gas turbine (GT) efficiencies crept upward from 15%, as E-class turbines matured into F-class. A decade ago, turbines were approaching combined-cycle efficiencies of 50%. The large, high-capacity G, H, and J class electrical GTs of today produce hundreds of megawatts of power. Used in combined-cycle power plants along with heat-recovery steam generators and steam turbines, they can achieve greater than 60% combined-cycle efficiency.
Large GT manufacturers have taken different approaches to increasing efficiency, including increasing overall mass flow, increasing compressor pressure ratio, and increasing the temperature of the air entering the turbine. The latter, increasing the firing temperature, is the most common and most technically challenging.
Natural gas turbines are not only being used as replacements because of their cost savings but also for their ability to meet stricter ambient regulations.
Hotter Is Better
As the temperature of the air entering the turbine has increased to be higher than the melting point of some of the materials that come in contact with hot gases inside the turbine, manufacturers have not only had to develop specialty turbine blade materials, but also new blade designs, coatings, and cooling technologies specifically to enable robust, reliable operations at these “ultra-high” temperatures.
According to Carlos Koeneke, vice president of project engineering and quality assurance at Mitsubishi Heavy Industries, many of these types of advancements have led the way for operation at turbine inlet temperatures of 1,600 degrees C, achieved during the last year.
“The biggest challenges with increasing the temperature were the materials exposed to the hot gases, which have historically limited the temperature in the past," he says. "We’re getting to the point where we can’t further improve the materials, and are now using thermal barrier coatings as facilitators. Also, internal cooling is now needed, which ‘steals’ some energy from the system but enables operatio.”
As a result of higher firing temperatures, mega turbines not only produce higher amounts of power, but higher power density as well, so fewer turbines are needed to generate the same amount of power. On a dollar-per-kilowatt/hour basis, the price is lower for mega turbines, since power plants actually spend less in construction, footprint, and installation.
Despite having high efficiency, these new GTs in combined-cycle power plants are challenged when it comes to operating efficiently under variable loads. Flexibility, which can refer to the ability to start and stop frequently or rapidly, is becoming more important as more generating plants receive power from sources such as wind and solar.
Achieving high efficiency in a combined-cycle plant requires operation at constant base loads or at “full load,” or peak operating conditions. “It’s not that long times are needed to achieve high efficiency, but they don’t react well to big changes,” Koeneke says.
Single-cycle GT systems that are faster to react are now able to operate more efficiently when “parked” at lower loads, and are also maintaining emissions compliance over wider load ranges. Some power plants are adopting multiple systems, both combined and single mode, for more flexible operations, since a single system cannot perform well in both modes.
Efficiency has long been the goal in designing and operating gas turbines. Having achieved greater than 60% efficient emissions-compliant operation, the new-era turbines are entering what could be referred to as “flexible efficiency,” as the focus shifts toward the ability to adjust to new types of demands for efficient operations.
Debbie Sniderman is a consultant, an engineer, and a contributing writer to Mechanical Engineering.
The biggest challenges with increasing the temperature were the materials exposed to the hot gases, which have historically limited the temperature in the past.
Carlos Koeneke, vice president of Project Engineering and Quality Assurance, Mitsubishi Heavy Industry
More on this topic
A University of Idaho Engineering Professor is conducting research that would determine generator model parameters at power plants.
Sophie Xu, a member of a team which participated in the university level X-Hab Academic Innovation Challenge, takes us through their creation and ...